ASHRAE Members around the world recently received their 2017 Fundamentals Handbook. Most of us likely received the digital version on a CD. Many of the new updates will impact the HVAC load calculations, performed by mechanical designers day in & day out – there are new design LPDs, revised kitchen equipment resources, and additional climate data, among many other additions! Something that hasn’t changed: load calculation methods.
The 2017 edition of the Fundamentals Handbook defines only two load calculation methods: the Heat Balance Method (HBM) and Radiant Time Series (RTS). As part of the introduction, the radiant time series is categorized as “a simplification of the [heat balance] procedure”, but what exactly is the simplification?
Heat gain from the sun offers an illustrative example. Solar energy is absorbed by the exterior wall of a building and transfers to the inside of the building by conduction. Because the wall has thermal mass, that heat isn’t transferred immediately – there’s a conductive delay.
Solar energy is transmitted to the inside of the building through the window. Some of the heat is absorbed and reflected by the window, and the remainder is absorbed by the interior surfaces. When those surfaces later emit that heat by convection, cooling load is created in the room – there’s a radiative delay.
The Heat Balance Method calculates these time delay effects explicitly with some basic assumptions like uniform surface temperatures. There are no arbitrarily set parameters. Conductive, convective, and radiative heat balance is calculated directly for each surface within a room.
By contrast, the radiant time series (RTS) calculation uses radiant time factors and conduction time factors to distribute hourly heat gains over a 24 hour period instead of iteratively calculating the time delay effects. A table of time factors published in the Handbook determines how long heat is held by a wall or other surface before creating a cooling load in the space.
Whether heat balance method or radiant time series is used to calculate heating & cooling loads, computer software is nearly always employed. IES Virtual Environment (VE) software performs ASHRAE load calculations using the non-simplified Heat Balance Method, calculating heat balance and the resulting loads directly without time factors. To learn more about calculating loads for HVAC design using the VE, check out www.iesve.com/loads.
ENTRUST is one of the R&D projects that IES is involved in under the Smart City banner. It’s part of the Horizon2020 call topic ‘LCE20: The Human Factor in the Energy System’, and seeks to develop an understanding of Europe’s energy system. In particular, it’s looking at how human behaviour and practices around energy is […]
Posted : June 28, 2017 by Rohan Rawte
Above from left to right: Ms. Carmen Lau, Ms. Heidi Hui, Ms. Ketki Phanse, Mr. Rohan Rawte & Ir. Cary Chan. IES has recently become a member of the Hong Kong Green Building Council (HKGBC), which represents a strong network of green building experts. This aligns with IES’ objective to help promote sustainability and green […]
Posted : June 26, 2017 by Edwina
In VE 2017, IES launched brand-new multiple simulation and optimisation capabilities. Designed to save you time and reduce project costs, these tools allow you to spend less time simulating and more time evaluating results. And that means increased value for your client, reduced error, higher quality results and the opportunity to integrate performance-led iterations and […]
Posted : June 26, 2017 by John G
This summer we’ve welcomed five female summer interns to the IES team – Galila Khougali (MEng Architectural Engineering, Heriot-Watt), Melanie Gines (MEng Architectural Engineering, Heriot-Watt), Agata Mamcarz (MEng Architectural Engineering, Heriot-Watt), Zoe Richardson (BSc Computing Science, Uniof the West of Scotland) and Ildiko Szabo (BSc Computing Science, Uniof the West of Scotland). As a STEM […]
Posted : June 8, 2017 by Karen Duffin
Over the past few decades, green building rating systems such as LEED and BREEAM have been firm fixtures of the global AEC industry and have helped the drive towards a more sustainable, resource efficient and environmentally conscious built environment. Whilst these rating systems have, to some extent, considered the comfort of the occupants using the […]
Posted : June 7, 2017 by Suzanne
The response from climate organisations, world leaders, large corporations and the general public to Trump’s removal of the US from the Paris Climate Change deal is encouraging. Looking at it in a positive light, it has taken the negative influence out of the picture and lets those who really believe and are truly passionate about […]
Posted : May 9, 2017 by Edwina
An article appeared in the Telegraph last week, Energy Scandal: Misleading Efficiency Claims Leading to Huge Bills for Homeowners. At IES, while we’re 100% in support of the industry needing to do much more to tackle the energy performance gap, we feel that this article unfairly lays the blame for it at the doors of […]
Posted : April 21, 2017 by Suzanne
We believe that much more needs to be done to mitigate climate change. It’s happening faster than anyone wants to believe. And buildings play a huge part in this. In fact, buildings are responsible for 40% of the world’s carbon emissions – that’s more than any other industry. If we are going to save the […]